for Palmer, TX
Re-inspected coil leak reported by another HVAC company. Leak verified will check warranty status of equipment for coil.
Heating and Cooling Installation
Installed Trane-TAM 7 Air Handler-4 Ton XR17 Heat Pump- Clean Effect Air Cleaner- Honeywell / Trane Touch Screen Thermostat
Checked Goodman Heat Pump Condenser and found bad contactor and 1/2 LB low R-22 freon. Replaced contactors and Added Freon
Garren replaced air filter and added 1.8lbs r22 freon