for Milford, TX
Checked Payne 2.5 ton heat pump upstairs unit, found 3 amp blown fuse, replaced. Checked outside unit found shorted out low voltage wires. repaired to proper working order.
We checked the indoor unit and started it up with a call from Tstat. Out door fan motor running, but no compressor. Capacitor was burnt up and depleted. We replaced 60/5 mfd capacitor. We checked the freon R22 levels and found out they were good. System returned to normal operation.
HVAC Service Call/ We found that the unit was frozen so we defrosted it and tested the pressure on the condensers. The unit was also low on R22 so we added 2.5 lbs.
HVAC Service Call/ Replaced blower motor
Low Voltage not working, Replaced Transformer and Fuse. Customer had Transformer already. Replaced 2-wire condenser wire on the AC Unit