for Midlothian, TX
Jennifer - Midlothian, TX
Very friendly.. Very prompt..very thorough
Great overall service!
Andrea - Midlothian, TX
Very pleased with H.E.A.T. Mechanical. The serviceman was on time, professional, and very thorough. Will definitely use them again.
Pam - Midlothian, TX
Janna - Midlothian, TX
Jim - Midlothian, TX
Great as usual
Susan - Midlothian, TX
Great service as always!
Damon - Midlothian, TX
The only company I will ever call for all my heating and cooling needs.
Jason - Midlothian, TX
Technician was nice and did a great job
Experienced & knowledgeable service
Frances - Midlothian, TX
Great service and friendly professional
Mary - Midlothian, TX
Your service gives me peace knowing my unit is in good working condition. I feel secure during the hot months of no breakdowns. I am so satisfied. Thank you
Mike installed secondary pan and safety float switch for Trane air handler
Checked 2 Carrier units, found a bad fan motor. Replaced motor, unit now cooling properly.
Heat pump not coming on, replaced bad wiring. Unit now working properly.
Water pipe burst in the attic. Home owner requested system inspection. -System showed no sign of water damage, all components were still operating within optimal parameters, and found no faults in the equipment.
Checked York 3 ton air handler. The fan would not shut off because of a bad control board, replaced within 2 days.
Concern of the condenser fan making loud noises. Checked system out and determined the blades had iced over due to freezing temperatures, when thawed out there will be no further issues.
Found failed breaker in main breaker box. Replaced 60 2pole Eaton type CH breaker. Power restored to system. Also, found failed heat strip contactor and replaced that as well.
Checked Goodman 95% gas furnace and found blown fuse, replaced. Installed HoneyWell focus pro 5000 1 heat 1 cool non programmable TsTat. 5 year warranty.
Repaired leak on high side freon line in the condenser. Pulled vacuum and recharged with 5 Lbs of 410 A freon.
Rough in Rheem heat pump system
We checked the Ruud Airhandler for vibration and we found a bad blower housing.
We did a tune up on the AC unit in the office and checked the Freon, AmpDraw motors and drains.
Checked indoor air handler, amp draw cleaned filters, checked blowers and housing. Found drain pan cracked, and will replace. Checked out door units freon, amp draw, cleaned coil and checked the capacitor. We returned on 4/11/17 and replaced warranty secondary drain pan.
Outdoor unit was running upon arrival. We did a full diagnostic on the outdoor unit. Found a bad Dual Cap 445, and replaced it.
We checked a 5ton York AC system and found a bad compressor.
We preformed an electrical check on all of the components including the Air Handler, compressor, and condenser. We also inspected the coils for signs of leaks as well as added 2lbs of R22.
We checked the A/C Condenser and found the pressure was running high and we checked the indoor unit coil, which was clean. Next, we found a bad TXV, so we quoted the customer on a replacement TXV.
HVAC Service Call/ We removed and replaced a 50 MFD Capacitor.
We blew out the drain line and installed a safety float switch.