for Maypearl, TX
Quick service at a fair price
Kenny - Maypearl, TX
Lisa - Maypearl, TX
They got to us really quickly. Did a great job and were reasonably priced. The only thing they didn't do was check my A/C filter to make sure it didn't need replacing. It did and after I changed it the house got considerably cooler. But I was happy at their response time and how quickly they fixed the problem. Just a small oversight as far as the filter.
Saved the Day!!
Clark - Maypearl, TX
Mike was great and made sure to communicate with us through our repair! All was fixed same-day!!
Great service and great prices!
Spradling - Maypearl, TX
Great fast service.
James - Maypearl, TX
They found out the problem with my air conditioner and quickly fixed it.
HEAT Mechanical always does and excellent job
John - Maypearl, TX
Tune-up great service
Israel - Maypearl, TX
Excellent work , and very very satisfied . I am going to help advertise ..
Fast service, trusty worthy
Randall - Maypearl, TX
Returns call in a timely matter, employees are very helpful.
Carey - Maypearl, TX
Checked the heat unit and had 5KW, but needed 10KW. We ordered the parts and installed heat strips.
Checked ice machine and found dirty condenser thermostat, cleaned off and checked rest of operation. Working in correct order.
Checked A/C unit and found dirty filters. Installed 20X25X1 pleated filters, also added 1/2 LB of R-22 Freon.
Maintenance. Rewired Tstat wire at the condenser. Checked Cap for compressor: BQuf tested and got 78.7 Checked the Cap for the fan and got 5uf tested 3.1 Replaced both Caps. Found unit low on R22 freon so we went ahead and placed more freon in the unit.
We cleaned out drain assembly, treated it with Pan Tabs, and also checked the freon levels.
We found and replaced a bad TXV as well as added 1.5 lbs of R22.
We moved the unit to horizontal and added duct supply and RTN. We also added low voltage, high voltage, a filter rack, extended drain, and a new supply of Plenum.
We installed a 5TON system and 2TON gas system.
We removed and replaced an evaporator coil and added 8+ lbs of R22 refrigerant.
HVAC Service Call/ We washed the condenser coil and checked freon levels.
HVAC Service Call/ We replaced a 3amp Fuse for this customer
We blew out the drain and added 2 couplings to the drains. We also replaced the AquaGuard Float Switch.
HVAC Service Call/ The compressor kept trying to restart so we removed and replaced a bad 50/5 capacitor at the condenser unit.
On August 1st we found the Air Handler frozen so we set the fan to on and turned the compressor off. We went back out the next day to recheck on the system. The Air Handler was now unfrozen and we added 3 lbs of R22.
Heating and Cooling installation/ Rheem 4 ton VS/AH and Duct work
HVAC Service Call/ Removed and replaced a condensor fan motor on their rent house
HVAC Service Call/ We removed and chemically cleaned the Evaporator Coil and Blower Wheel