for Mansfield, TX
We checked the Trane AC system that was not cooling during the heat of the day. We found the A-coil was very dirty so we chemically cleaned it.
We found that the unit was froze up and we found a bad TXV Air Handler. We replaced the TXV and added 1 lb of R22.
AC Unit not cooling- replaced capacitor, Checked amp draw on ODF and Comp. also checked freon levels-everything looked great