for Grandview, TX
Repair of Trane air handler
We checked the Trane Airhandler and found a bad fan control bard. We replaced the control board and the unit began working properly.
ADDED 3LBS OF R22 FREON
80/5 MFD Warranty capacitor
Added 1 1/2 LB'S of R-22 freon to AC System