for Arlington, TX
HVAC Service Call/ We replaced the failed furnace ignition control
The evaporator coil was dirty so we chemically cleaned it and we also cleaned out the condensate drain.
We changed the filters for their quarterly PM, replaced an A-39 belt on the front AC Unit and also replaced a belt on the office unit.
Installed Copeland R-22 Compressor, New Capacitor and Recharged with Freon.
AC Unit not cooling. Added 1LB 410a Freon. 17.3 degree split was 13 degree split. Pressures look good. Checked Heat Strips.